resistance to earth of a plate R in ohms (code of practice earthing history First published as CP First published as BS BS Code of practice for protective earthing of electrical installations. 16/22 Total Solution to Earthing & Lightning Protection | 9AKKA Technical BS Code of practice for protective earthing of electrical.
|Published (Last):||15 November 2006|
|PDF File Size:||15.36 Mb|
|ePub File Size:||15.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
Measurements of the soil resistivity for the pre-determination of the resistance to earth or the impedance to earth should be carried out using a four probe method widely known as the Wenner method as follows. There are commercially available materials to achieve this effectively, but care should be taken to understand how they work during installation to ensure that they remain in contact with the rod or strip and do not shrink or swell away after drying out.
Please download Chrome or Firefox or view our browser tips. The value of resistance required might not always be amenable to an automatically set value. There are many configurations that can be set out under this heading, but a few of those which one is most likely to try first in order to achieve the required value are included especially when dealing with deep reinforced piles, etc.
However, onsite resistivity testing should always be carried out prior to carrying out an earth system design and installation. A waterlogged location is not essential unless the soil is sand or gravel. Ideally confirmation of the combined resistance of all the electrodes should be obtained, but the earth resistance of a structure covering a large area ba7430 be quite low and an accurate measurement on a completed structure might be difficult or impossible to achieve. Chemical treatment of soil has environmental implications and should not be considered as a long term solution in order to meet a specified level of hs7430, apart from the risk of corrosion to the earthling system.
Connections to the plate should be by copper conductor, welded, riveted or otherwise attached with material that will not cause corrosion at the joint.
The products of corrosion occupy ppractice greater volume than the original metal and cracking might occur. Columns 2 and 3 relate to most of the British Isles, but column 5 is more specific to marshy flats around river estuaries.
Click to learn more. This is one of the best design reference i have seen. When two or more strips in straight lengths, each of length L in meters m and a separation distance s metres are laid parallel to each other and connected together at one end only the combined resistance may be calculated from the following equation:.
Earhing is of particular relevance to: The resistance to earth of a given electrode depends upon the electrical resistivity of the soil. Take the smart route to manage medical device compliance.
The effect of shape on an bs430 resistance is related to the current density around the particular electrode considered. Facebook Linkedin Google Plus Twitter.
Premium Membership Get access to premium electrical guides, technical articles and much more! Wherever significant continuous earth leakage current is expected, it is recommended that a main electrode of the types described in previous section be provided to which the foundation electrodes can be bonded to provide auxiliary electrodes, thus giving assistance to high fault currents.
Second important characteristic of earthing connection is that it MUST be capable of carrying the maximum expected fault current. Premium Membership Premium membership gives you an access to specialized technical articles and extra premium content electrical guides and software.
Professional in AutoCAD programming.
It is important to ensure that their resistance areas do not overlap. This applies particularly to surfaces which might practcie been primed before assembly. Current should be passed between the two outer electrodes and the resistance R may be found as the ratio of the voltage between the inside electrodes oof the current conducted through the outside electrodes. It also defines selection parameters for the earthing arrangements and makes clear the need for careful consideration of various site conditions such as soil composition and resistivity.
They may be used to give an indication of the difficulties that one might face in preparing an adequate design at the chosen location.
Thus a pipe rod or strip has a much lower resistance than a plate of equal surface area. It is essential to measure the resistance to earth of any metalwork it is intended to use as an electrode, and to monitor its cove at regular intervals afterwardsin order to confirm that it continues to provide an adequate connection to earth.
The resistance to earth of concrete encased steelwork or of concrete reinforcing bars varies according to the type of esrthing, its moisture content, and the design of the foundation.
Foundation metalwork in concrete may be used as a ready made and effective earth electrode. Dry sand, gravel, chalk, limestone, whinstone, granite, any very stony ground, and all locations where virgin rock is very close to the surface should be avoided if possible.
This is a amendment to a British Standard on how to meet UK electrical installation earthing requirements.
You may find similar items within these categories by selecting from the choices below:. It is important that consideration is given to the possibility of corrosion of the metalwork reinforcement. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3.
This is related to the hemispherical radius of the rod and that has avoided the effects of using less than tor two-times constraint in design thinking.
Learn more about the cookies we use and how to change your settings. Overview Product Xode What is this standard about?
Corrosion of concrete encased steelwork, subject to a. The standard is relevant in the following sectors: This model is more closely aligned to the basic sb7430 behind the electrostatic behaviour of an earthing system componentin effect stating more clearly the interactive effect of the value of s which for practical purposes has long been set as being not less than twice the depth of the rod.
It may be considered necessary to apply numerical methods which are more complex than the formulae given below and software is available to carry out the more detailed calculations.
Rpactice who bought this product also bought BS EN The resistivity so determined applies to an electrode separation distance a, which is related to the depth of investigation.
The total electrode area formed by the underground metalwork of large practjce may often be used to provide an earth resistance lower then that obtainable by other methods. Above ground and at anchor bolts it may generally done by attaching a bond conductor earthiny bypass each structural joint. Soil temperature has some effect on the upper layers of strata, but is only important under frosty conditions. Standard Number BS Most first approximation formulae are related to homogenous soil, which is rarely the case in practice, where the different layers of strata will affect the distribution of current passing through the electrode.
The purpose of earthing System earthing involves the provision of a connection to the general mass of earth.